How to manage the elevator by access control controller?
Elevator management by access control controller.
Elevator management is a kind of elevator control technology. A similar “access controller” system device is installed on the original elevator.
Only after the card is swiped, the elevator will be started and the cardholder will be sent to the floor to be reached.
The composition of the elevator management system: access control server, access control authorized client, access controller, access control card reader.
There are three modes of elevator management by access control system:
1, Mode one: Swing card calling mode：
The card reader is installed on the passage (outside elevator box), cardholder swipes the card ( or press the up and down button after swiping it.
The authorized cardholder can get in the elevator, no authorized or without card can’t get it in.
Implementation: Use the relay of access control system to control the on/off button or the public line of two buttons.
2, Mode two: Swing card to press floor with the right
The card reader is installed in the elevator, the holder can press the floor button after swiping card, no swing card and no authorized holder can’t press the button
Implementation: Use the relay of access control system to control the public line on/off for all the floor.
Remark: If the elevator box is metal, it will shield and reduce the card reading distance (or even can’t work). It is recommended to make it 1-2 centimeters higher
or choose a card reader with strong metal attenuation capability.
3, Mode three: Swing card to the signed floor：
The user of which floor, will be sent to the singed floor automatically after swing card. Security guard, press the required floor after swing card.(same as Pattern 2)
Implementation: it is necessary to use a special elevator door access control system controller with dozens of relays. Each relay controls a floor button and the proximity card is authorized to the corresponding floor.
This demand is not popular. It is used only in very few buildings, such as high-end residential buildings and some of several floors, which is rented by a company and has few visitors.
The fire passage must be closed, otherwise, the others can go it through to the floor where he wants. Closed the fire passage is not good for inspection and safety. It can’t manage the floor independently if open it.
This method of work is not humanized, such as a high-end residential building, the people from 19th floor wants to drop around a new friend’s home on the 30th floor. They must go to the first floor together. Then the people from 30th floor take the people of 19th floor to his home. It is very inconvenience, just a concept.